12pcs/carton carton size:53*43*29.5cm
CE RoHS TRUMP universal voltage AC100~240V ozone generator SPA ozone for water purification
1 - 1000
To be negotiated
CE RoHS TRUMP universal voltage AC100~240V Corona Discharge Ozone Generator for Pool and Spa
1) Ozone generators for water treatment industry such as private swimming pools, ,hot tub,spas, drinking water, water taps, and showers,fish tank
2) Air treatment like culturist, hospitals, hotels, meeting rooms and refrigerators
IP: AC100-240V AC120V AC220V
Ozone output: 50-300mg
Function: Water purification,water detoxification
TCB-109 is a reliable and flexible system designed to generate ozone for your private pool or spa. It has Universal Auto-range Voltage that can operate with any input voltage (200-240 VAC and 50/60 Hz).
Below picture shows the basic layout recommended for the installation of TCB-109. please kindly obey below steps to finish the installation of ozone generator. 1.Turn off all power. 2.Loop the hose into a “Hartford Loop” and have the upper part of the loops positioned above the water line level as shown in picture. Attach the hose to the ozone injector fitting on the spa plumbing. Install the check valve on the hose.When you install the check vlave,there is an arrow on the check valve,make sure that the arrow points in the direction of air flow from the generator to the ozone injector . Note:If you do not properly install the check valve, the air flow will be blocked from going into the spa/pool ,water may flow back to the ozone generator via hose ,cause the ozone generator will not perform the ozonation process. Note:If the supply cord is damaged, it shall be replaced by the manufacturer or its service agent or similarly qualified person in order to avoid a hazard. 3.Power up the system and briefly run the filtration pump. Place your finger over the end of the hose near the check valve. You should feel a slight suction. If not, check for hose kinks, hose obstructions, and that the check valve is in the proper direction. When suction is obtained, attach the hose from the generator to the barbed output of the ozone generator. 4.Turn off the control system and hook the power cable to the control system marked for Ozone. (Follow the system’s wiring diagram for the proper location.) 5.Turn the system power back on and run the pump. Confirm that the light in the Ozone window is ON.