Battery(Over Voltage,Low Voltage,Input Short Circuit)
DC Output (Over Current ,OverLoad,Short Circuit)
Over Temperature Protection
PV Input Oppose / Battery Input Oppose
Standard Modbus Agreement
Temperature Protection Value
Machine 85℃/Air Temperature55℃
Supporting Battery Type
Lead-acid Batteries,Nickel-hydrogen Batteries
Nickel Cadmium Batteries, Lithium Batteries
(Other Battery Type can customize)
Dot matrix LCD screen
Capacitive touch button
Above technical parameters are in 25 ℃
Remote Dispaly and PC control program
1. Availaable for 1 KM
2. LCD screen synchronous display parameter.
3.Can parameter settings ,Control DC load
output and Fault reset operation ect.
4.Capacitive touch button ,Higher service life and
tightness.Suitable for dust environment
1. Support Multimachine Parallel Communication
2. Synchronous display running state and parameter
3. Can setting parameter, Control DC loads output
and Fault reset operation ect.
4. Communication module directly contact withPC
USB port ,Support WIN XP / WIN7 / WIN8.
CE,RoSHAND FCC APPROVALS CNBOU products are stricily according to international standards And if enables us to provide 2-years quality warranty
Yueqing Bou New Energy Technology Co.,Ltd is a high-tech enterprises specialized in research and development,production and sales in the line of green energy saving products.The hot products are solar&wind power pure sine wave inverters,solar controllers,charge&bypass sine wave inverters.
Packaging & Shipping
> We accept T/T,Western Union or Paypal before Production .
> If have any comments about payment, please contact us .
> 3-15 working days after received the payment receipt (based on actual quantity)
> Tracking No. will send to you by email.Enclosed the packing&testing photo before
shipment for your reference.
How to choose suitable inverter?
If your load is resistive loads, such as: bulbs, you can choose a modified wave inverter. But if it is inductive loads and capacitive loads, we recommend using pure sine wave inverter. For example: fans, precision instruments, air conditioner, fridge, coffee machine, computer, and so on. Modified wave can be started with some inductive loads, but effect for load using life, because capacitive loads and inductive loads need high quality power.
How do I choose the size of the inverter?
Different types of load demand for power are different. You can view the load power values to determine the size of the inverter.
Notice: resistive load: you can choose the same power as the load.
Capacitive loads: according to the load, you can choose 2-5 times power.
Inductive loads: according to the load, you can choose 4-7 times power.
How connection between batteries and an inverter?
We usually believe that cables connecting battery terminal to inverter shorter is better. If you are just standard cable should be less than 0.5M, but should correspond to the polarity of the batteries and inverter-side outside. If you want to lengthen the distance between battery and inverter, please contact us and we will calculate the recommended cable size and length. Due to long distances using a cable connection, there will be a reduced voltage, which means that the inverter voltage would be far below the battery terminal voltage, this inverter will appear under voltage alarm conditions.
How to calculate the load of working hours requires configuration of the battery size?
We will usually have a formula to calculate, but it is not hundred percent accurate, because there is also the battery's condition, the old batteries have some loss, so this is only a reference value:
Work hours = battery capacity * battery voltage *0.8/load power (H= AH*V*0.8/W)
How to choose a solar controller?
At present, solar controller have MPPT and PWM. According to our actual test data, conversion efficiency of the PWM controller normally less than 70%, MPPT controller conversion efficiency is about 95-97%. MPPT solar controller is expensive than PWN solar controller, but the price of solar module are more expensive. Using MPPT controller, you can reduce the solar module, save the cost of the entire system
How to choose a suitable MPPT solar charge controller?
CNBOU MPPT solar controller support PV input voltage 18V-150V, DC 12V 24V is automatic identification. You just need according to battery capacity to select different charging current controller.
How to Contact Us right now?
Send your inquiry Details in the Below.Then Clik "send".